Foundation Repair Newark
Newark structural foundation problems in your house, garage, or commercial building can cause one or more of the following observable symptoms or conditions: (Actual example of a Newark foundation repair job is detailed below.)
- floors out of level
- cracks in walls (especially above doors and windows)
- sticking doors
- sticky windows
- cracks in concrete walls
- cracks in brick walls
- crack or cracks in perimeter foundations
- cracks in driveways
Foundation Repair Causes in Newark
Structural foundation problems typically found in Newark by specialists can be caused by one or more of the following conditions for which repairs may be called for by your architect, engineer, or general contractor:
- Poor drainage problem (wet soaked soil, mud, muddy under house)
- Bad smell in basement or crawlspace caused by mold or mildew
- poor grading
- deficient underpinning or underpinning needs replacment
- earthquake or earthquakes
- land movement or landslide
- failed retaining wall problem
- expansive soil like the clay soil found in the bay area (that expands and contracts with soaking and drying)
- rotting beams
- rotted posts
- wet crawl spaces, where soil is soaked under the home
If you find any of the above on your property, you need a qualified contractor or structural engineer to inspect, and give you a free inspection report, or free estimate, so you can discover the best way to repair or fix the problem at the lowest cost. For your inspections, be sure and choose a foundation repair construction companies, engineering firms, or specialist expert inspectors that specialize in foundation repair work, and can provide the necessary permit or permits. We are a Bluebook listed foundation repair construction company you can rely on.
Heres an example of a foundation repair job we did in Newark :
Enclosed is a copy of the recent floor level survey done at your home showing it to be 1.8 inches out of level.
The sub-area of your home was wet at the time of my visit, which may be causing some of the recent movement in the floors. We will construct a drainage system along a 22 feet long portion of the rear and left sides, and the front side up to the entry. The portions along the front and rear sides will be constructed in the planters with an average depth of 32 inches.
The drainage system consists of two pipes in a rock filled trench. One is perforated, to collect sub-surface water and the other is non-perforated, to collect water from the roof downspouts. At the upper end or start of the perforated pipe, a clean-out will be provided so the pipe can be tested or cleaned as necessary.
The minimum depth for the perforated pipe will be below the grade of the soil under the house and both the perforated and non-perforated pipe will fall at least 1/8 inch per foot for the total length of the system to the point of discharge.
The perforated pipe will be installed on top of a bed of gravel, two inches deep, with the perforations pointed down. The trench will then be then backfilled with drain rock. The rock we recommend is Class I, Permeable Type A drain rock per the California State Specifications. The drain rock is clean gravel that varies in size from 1/4 to 1/2 inch.
The trench will be a minimum of 12 inches wide. This permits a four inch blanket of rock on each side of the four inch perforated pipe.
The system will discharge through a 4 inch solid pipe across your front yard to the street.
We will cut the sidewalk, install a drain pipe under the sidewalk and through the curb to discharge into the gutter, and repair the concrete.
We will remove and replace a strip of concrete along the left side as necessary.
Whatever foundation repair or structural problem in Newark, call Ward Construction for a free estimate and expert opinion.